|Place of Origin:||Jiangsu|
|Minimum Order Quantity:||64PCS|
|Packaging Details:||inner box: neutral packing with label; 64pcs/ctn|
|Delivery Time:||10 workdays|
|Payment Terms:||Western Union, T/T, Paypal|
|Type:||Electric Heating Controller||Voltage:||220V/230V|
|Power Consumption:||2W||Housing Material:||Self-extinguishing PC|
|Ambient Temperature:||-5-50℃||External Limi:||5-60℃(factory Setting 35℃)|
Heated Floor Digital Temperature Control Electric Heating Thermostat
For the control of warm-water(floor) heating systems and direct electric heating systems used in Commercial buildings, Residential buildings, Light industrial buildings...
Setting range: 5~35℃
Limitation range: 5~60℃ (factory setting:35℃)
Switching differential: ±0.5℃-10℃
Ambient temperature: -5~50℃
Protective housing: IP20
Housing material: self-extinguishing PC
Floor sensor: rubber-thermoplastic NTC sensor, cable length is 3m
Individual white box and outer carton, 64pcs in one carton
Switch off after finish the advanced setting, the modified function will operate in re-open. Please modify setting carefully.
EO: Built-in sensor short-circuited or disconnected.
E1: External sensor short-circuited or disconnected.
When shows E0/E1 error, thermostat must be checked till the error is eliminated.
1, Release the front cover by inserting a screw drive into bottom crack.
2, Take the backing plate apart according to the following diagram.
3, Mounted the backing plate in the wall socket by screwdriver.
4, After connect wires (see right diagram), the thermostat mount on the backing plate and remounted the cover and frame.