Payment & Shipping Terms:
|Type:||Floor Heating Systems||Voltage:||230V|
|Setting Range:||5-60℃ (can Adjust To 35-90 ℃)||External Limitation:||5...60℃(Factory Setting: 35℃)|
|Housing Material:||Anti-flammable PC||Installation:||Wall Mounted Installation|
underfloor heating room thermostat,
underfloor heating programmable thermostat
Digital Underfloor Touch Screen Heating Programmable Thermostat
Weekly circulation digital programming touch screen thermostat with LCD screen, which has 6-event everyday. Manual mode and programme mode could be selected.
For the control of warm-water(floor) heating systems and direct electric heatings systems used in Commercial buildings, Residential buildings, Light industrial buildings.
Choice of 7 day, 5/2 day programmable or
non-programmable (installer selectable);
6 time and 4 temperature settings every day;
pre-programmed or personalized schedule;
Energy saving up to 33%;
Data memory when power is off;
Large, touchscreen display;
European standard installation box;
White lighted display for easier low-light viewing;
5+2 or 6+1 or 7 days six periods program schedules maximize comfort and economy;
Comfort & Convenience
Intuitive menu-driven set-up, programming and operation,
Enhanced touchscreen security prevents tampering.
Can switch upto 16 amps (230v)
Temperature display resolution: 0.5 C;
A / AF/ F models all in one
Combination of 3 models;
A - Air only, with built-in sensor;
F - Floor only,controls floor temperature;
AF - Controls air temperature with ability to limit the
Each thermostat is equipped with built-in sensor
and a 3 meter floor sensor. The floor sensor can be extended.
|Power supply||230VAC (120VAC optional)|
|Inputs||2 x NTC10K temperature sensors|
|Output||1 x switch relay(R1),max 3500watts|
|Ambient temperature||0 °C [+32 °F] ~ +45 °C [+113 °F]|
|Operating RH||0~95% (non condensing)|
|Dimensions||86mm x 86mm x14mm|
|Backlight life||5,000 hours|
1pc/inner box, 50pcs/carton
Carton size: 51x22x36cm
All thermostat installations should be carried out by a fully qualified electrician.
To avoid electrical shock and to prevent damage to the thermostat,disconnect the power supply before beginning work.
Electrical wiring regulations prohibit the thermostats from being installed in bathrooms;if using the thermostat in a bathroom,install the thermostat on an internal wall outside the bathroom as close to matting power supply cables as possible.
Do not switch on the system before the substrate(e.g.concrete)and floor covering(e.g.tile adhesive)are completely dry to avoid cracking.