|Place of Origin:||Jiangsu|
|Minimum Order Quantity:||40pcs|
|Delivery Time:||10 workdays|
|Payment Terms:||T/T, Western Union,Paypal|
|Supply Ability:||3000 pcs/week|
|Media Temperature:||1~95℃||Control Signal:||On/off,2 Position,spring Return|
|Nominal Pressure:||1.6Mpa||Close-off Pressure:||0.2Mpa|
|Full Stroke Time 'on':||Approx. 10s||Full Stroke Time 'off':||Approx. 5s|
heating motorised valve,
motorised water valve
|Power supply||220~240VAC 50/60Hz|
|Full stroke time 'on'||approx.10s|
|Full stroke time 'off||approx.5s|
1.Inlay contact switch, the motor is power off after the valve completes open and close, so it has long service life and power saving, but is also safe.
2.The valve body is separated with driver, could be disassembled rapidly.
3.The valve body structure is unique, is allowed of big pressure difference.
4.The driver has manual controller is available for system debugging and maintenance, the manual opening is about 70% (push down the white driving arm to the bottom, and then push inside, when the power is recovered, the valve and driver will return to automatic position)
5.B type driver has inlay relay, one-line control and three-speed switch, realize multi valves parallel, and match with various temperature control switches. (special for four-pipe)
6.Select ordinary driver, one temperature controller matches only one electric vale, or any results caused will be nothing with manufacturer.
Pipe Connecting Instruction
Motorized control valve should be mounted on cold/hotwater inlet or outlet pipe of fan coil unit for opening orclosing cold /hot water. The actuator is controlled by theroom thermostat.
2-way valve(see Fig 1) is installed on cold/hot return water (CHR) pipe , when de-energized, the rubber insidenormally closed at port "B" , stop water flow. when energized, the rubber moved from port "B" to the centerof port "B" & "A" and cold/hot water flow through 2-wayvalve to return water pipe.
When the actuator is de-energized, spring returnmechanism drives valve to normally closed position,port "B" is closed . Cold/hot water inlet from port "AB"(bottom)by-pass to port "A" to return water pipe ,
when energized , rubber is moved from port "B" to port"A" and closed. Cold/hot water inlet from port "AB"through port "B" to fan coil unit then outlet to returnwater pipe.
1.Goods will be delivered within 10 working days after the payment received.
2.We ship item via DHL, Fedex,UPS,Door to Door service express or air and sea.
1.Reply your inquiry in 24 hours.
2.Experienced staffs answer all your questions in fluent English.
3.Customized design is available.OEM&ODM are welcomed.
4.Exclusive and unique solution can provide to customer by our well trained and professional technicians.
5.Special discount and protection of sales area provided to our distributor.
1. All products we sell are in good quality and have been tested before they are shipped out.
2. We offer 1 year Warranty and 3-year after-sales.
12h online chat
Welcome to your inquiry!